Post your questions and comments here.
2 posts • Page 1 of 1
- Posts: 1
- Joined: Fri Nov 02, 2018 9:59 am
Is it possible on the BM 2000 to convert the G wire to a C wire and jump the Y to G at the EWC control panel? I saw this in a Honeywell video. I'm aware I will lose access to the manual fan control but, per Honeywell video, the fan will still operate when the heat or AC is activated. I have an oil fired forced air furnace (no heat pump) and have no c wire at the thermostat. Thermostat wires include RC RH G W Y (RC is jumped from RH).
You do not have the required permissions to view the files attached to this post.
- Posts: 207
- Joined: Thu Dec 08, 2011 3:05 pm
Give a call and we will talk 18004463110X490